If you want to install underfloor heating in a room with a low height or in places where the supporting structure is less strong (wooden subfloors). It provides a dry construction system solution. The system consists molded EPS insulation which steel heat distribution profiles are installed.
The aluminum Omega profiles distribute the heat from the underfloor heating system on the floor and placed on top of the 25mm dry construction insulation. Due to the high thermal conductivity of the plates the reaction time is much lower compared to traditional systems (thermal conductivity: 80 W / mK).
As a general rule for ordering you can use approximately 8 profiles per m2.
Note: When you use these profiles in combination with the dry construction insulation than use a underfloor heating pipe
with a diameter of 14mm.
Dimensions: 0,75m. per insulation board
(100cm x 75cm)
Units per box: 23 sheets (17,25m.)
Distances tube: 125mm (main heating)
Maximum pipe length: 100m
Omega aluminum profiles
Dimensions Profile: 1000mm x 120mm
Thermal conductivity: 80 W / mK
Necessary profiles: approximately 9 profiles per m2.
MAGNUM DryFloor 25mm 10 pcs/7,5m.
Aluminium Omega-Profile for 14mm tube 1000x120x0,4mm
MAGNUM Tube underfloor heating tube
MAGNUM Tube PE-RT 14 x 2 – 120 m
MAGNUM Tube PE-RT 14 x 2 – 240 m
MAGNUM Tube PE-RT 14 x 2 – 600 m
Adaptor / Eurokonus connection fittings 14 x 2 x 3/4